UL Standard for Safety Central-Station Alarm Services Seventh Edition
适用范围：1.1 These requirements apply to:a) Central-stations providing watchman, fire-alarm, and supervisory services as described in theNational Fire Alarm Code, NFPA 72;b) Central-station burglar-alarm systems intended and specifically designated for burglaryprotection use at mercantile and banking premises, on mercantile safes and vaults, and onbank safes and vaults; andc) Residential monitoring stations monitoring residential alarm systems.1.2 These requirements apply to central-stations, subsidiary stations and residential monitoring stationsthat are intended to be located in buildings constructed in accordance with building codes, such as theBuilding Officials and Code Administrators (BOCA) National Building Code, the Standard Building Code,and the Uniform Building Code.1.3 The central-station burglar- and fire-alarm station and residential alarm systems covered by theserequirements are systems in which the operation of electrical protection circuits and devices are signaledautomatically to, recorded in, maintained in, and supervised from a central-station or residential monitoringstation having trained operators and runners on duty at all times.1.4 Requirements covering the construction and operation of burglar-alarm units used in theburglar-alarm systems covered by this standard are contained in the Standard for Central-StationBurglar-Alarm Units, UL 1610, and the Standard for Digital Alarm Communicator System Units, UL 1635.1.5 Burglar-alarm protective devices installed on individual properties are classified as to the extent ofprotection at each location. Requirements covering installation and classification (of extent) of alarmprotective equipment at individual locations are contained in the Standard for Installation andClassification of Burglar and Holdup Alarm Systems, UL 681.1.6 Requirements covering the construction and operation of fire-protective signaling equipment used inthe systems covered by this standard are contained in the Standard for Control Units and Accessories forFire Alarm Systems, UL 864.1.7 Systems covered by these requirements operate within the limits of the National Electrical Code,ANSI/NFPA 70, as applied by the local authority having jurisdiction. The Articles of the National ElectricalCode that apply are:a) Article 725, within the limits of Class 2 or Class 3 remote-control and signaling circuits forburglar-alarm systems;b) Article 760 for fire-alarm systems;c) Article 800 for outside wiring and protectors; andd) Article 820 for protectors for radio antennas.1.8 Requirements for software and hardware, and the installation and operation of an automation systemin a central-station, subsidiary station or residential monitoring station are covered by the Standard forCentral-Station Automation Systems, UL 1981, or by the Standard for Control Units and Accessories forFire Alarm Systems, UL 864, and/or the Standard for Central-Station Burglar-Alarm Units, UL 1610.1.9 A reference made to ²station² refers to a central-station (burglary or fire), subsidiary station orresidential monitoring station, depending upon the context in which it is used.1.10 These requirements do not cover the communication channel between the protected property andthe station. This includes:a) The company that provides the communication channel andb) The equipment that is used to provide the communication channel.Exception No. 1: If the communication channel is owned and operated by the station, these requirementsdo apply.Exception No. 2: These requirements do apply to an alarm and signal transport service company.
网络出版服务许可证：(署)网出证(京)字第072号 互联网药品信息服务资格证书号：(京)-经营性-2016-0015 信息网络传播视听节目许可证 许可证号：0108284